In the pipeline - Information Blog # 57 CCTV DRAIN INSPECTION -BRIGHTON
February 15 2016
Case Study 2….
JET CLEAN AND CCTV SEWER
Attended property on 04/02/16 to carry out jet clean and CCTV inspection of sewer.
FINDINGS/ACTIONS -Accessed property and set up CCTV inspection equipment -CCTV inspection the main sewer line and all lead off drains to locate problem areas -Set up jet cleaner and cleaned all mass tree root entry points -Re-inspected and found certain sections of tree roots had not cleared due to severity -All major issues appear to be behind unit 4 -Unable to get access to courtyard to carry out navi-track location works -The remainder of the drain is in okay condition, with only minor tree root points found which were cleared during jetting works -Packed up and left site clear
RECOMMENDATION 1. Jet clean using industrial size jetter and re-line the drain before roots have the chance to re-infest.
Call webbplumbing services on 1300 238 993 and we will assist with any drainage problems….